POWERHARD M RVhMVh-K cable has been specially designed for installations in potentially explosion hazard locations (ATEX), provided that local regulations allow it. It is highly recommended for petrol stations, petrochemical plants, flammable product warehouses, etc. It can also be used in installations such as production plants, agricultural facilities, street lighting and installations in general where the cable is subject to high mechanical aggression.
This cable is also available in hydrocarbon resistant version.
POWERHARD M RVhMVh-K cable performance
LOW VOLTAGE 0,6/1kV
BUREAU VERITAS / CE / RoHS
CPR Construction Products Regulation
Maximum service temperature: 90ºC.
Maximum short-circuit temperature: 250ºC (max. 5 s).
Minimum service temperature: -40ºC (fixed and protected installations).
Minimum installation and handling temperature: 0°C (on cable surface).
Flame non-propagation based on UNE-EN 60332-1 and IEC 60332-1.
Reaction to fire CPR: Eca, according to EN 50575.
Reduced halogen emission. Chlorine <15%.
Minimum bending radius: x10 cable diameter.
Impact resistance: AG4 High severity.
Chemical & Oil resistance: Good.
UV Resistant: UNE 211605.
Potentially explosion hazard locations (ATEX).
Water resistance: AD7 Immersion.
Meter by meter marking.
Potentially explosion hazard locations. (ATEX)
POWERHARD M RVhMVh-K cable design
Electrolytic copper, class 5 (flexible), based on EN 60228 and IEC 60228.
Cross-linked polyethylene insulation type DIX-3 according to HD 603 and XLPE according to IEC 60502-1. The standard identification of insulated conductors according to HD 308, is the following:
1 x Natural
2 x Blue + Brown
3 G Blue + Brown + Green/yellow
3 x Brown + Black + Grey
3 x + 1 x Brown + Black + Grey + Blue (reduced cross section)
4 G Brown + Black + Grey + Green/yellow
4 x Brown + Black + Grey + Blue
5 G Brown + Black + Grey + Blue + Green/yellow
6 G or more Brown + Black numbered + Green/Yellow
Galvanized steel wire armour. Aluminium armour is used in single-core cables to avoid parasite currents that may overheat the cable.
PVC outer sheath type ST2 according to IEC 60502-1. Black colour.